Why is my Floor Temperature Reading Incorrect?
3iE Energy-Monitoring Thermostat
If your floor probe reading significantly varies from the actual temperature of the floor, the sensor probe and cold tail lead may be in the same conduit. Putting both in the same conduit can cause interference with the probes temperature reading, which can cause inaccuracies.
Setting your thermostat to read the air temperature will fix the problem. However, we suggest correcting the conduit issue by installing your sensor probe in a separate conduit. Certainly, install the sensor probe as outlined in the installation manual. This would be suitable for a more accurate program.
Explore our YouTube channel videos below:
Subscribe to our YouTube channel here.