How To Wire the DS-2C Controller?
DS-2C Outdoor Snow Melting Controller
Below, you’ll discover a brief video guide on how to wire the DS-2C, or you can refer to written instructions for guidance.
For more videos, subscribe to Warmup Inc on YouTube.
TYPICAL LOAD WIRING OF THE DS-2C CONTROLLER
The yellow load leads are N.O. contacts and do not supply power directly to your load. The relay inside the controller acts as a switch. While not as convenient as directly supplying power for the load this allows you to operate the DS-2C from one voltage while controlling a load of a different voltage without adding an external relay or contactor.
For example, the DS-2C can be powered from 120VAC but can directly control a 24VAC signal for a boiler system or 277VAC for the heating wire.
The following diagrams show a possible wiring scheme for connecting the controller to your load. Your load may be a direct connection to heat cable, a heater, a contactor coil, or a control voltage. For clarity, the green safety GROUND leads are not shown.